This solution will prevent contact between the metal and the corrosive material by creating a sticky and non-moist organic layer on the metal surface. The mechanism of the Mitreh 764 solution is that the hydrophilic head of the amine molecule is attached to the metal and the other end of the molecule is hydrophobic and prevents corrosive substances in the water from reaching the wet section of the metal. The amount of injection of this solution is very important because high dosage injection, poor distribution or low injection dosage can cause exacerbate corrosion problems.
Calibration of Using Mitreh 764 Solution:
In order to prevent corrosion in closed medium boiler systems due to the using sensitivity of this solution contact technical experts of Abrizan Company.
In the first few weeks of use, this inhibitor should be used at a rate of two to three times that of normal to produce the best film on the whole metal surface (primary treatment).
Some Physical Properties of the Solution:
|Liquid||Physical state||10.1 – 10.7||pH|
|Colorless||Color||96 – 98||Boiling temperature range (˚C)|
|Mild odor||Odor||-2 – 0||Freezing temperature range (˚C)|
|1.001 – 1.013||Density at 20˚C (gr⁄ml)||Dissolves rapidly||Solubility in water|